Maintenance release of 670 series Ver. 2.1 IED modules (18.104.22.168)
A new revision of the IED modules for 670 series version 2.1 has been released. The revision designation of the IED modules is 22.214.171.124.
The following issue has been corrected in the new revision:
Recommendation to update
- Comparator function, REALCOMP
It was reported that the second input at the comparator function REALCOMP could allow invalid datatype connections. Incorrect datatype definitions of the second input in the IED modules prevented a read back of 670 series version 2.1 configurations.
By installing and using the new corrected IED modules revision 126.96.36.199, this read back issue is corrected.
If the comparator function REALCOMP is used in configurations, it is mandatory that the new IED modules for 670 series 2.1 is used.
IED Connect support
Updating to the new IED modules does not require any changes in the installed IED Connectivity Packages for Relion® 670 series. The connectivity packages are available via the PCM600 Update manager.
Delivery of the IED modules
The updated revision of the IED modules are available via the PCM600 Update manager.
Global Product Manager
Grid Automation Products